Orifice plates have long been used for measuring and metering airflow. Fixed orifices are used to measure
airflow in laboratories and for balancing duct runs in industrial applications. Orifice plates are sized
for a particular amount of airflow to pass through, given the upstream static pressure.
To be useful as a device for measuring airflow, an orifice plate is mounted in a tube with two pressure
taps, one on the upstream side and one on the downstream side. This device is an airflow meter. The pressure
tap nearest the fan is called the high pressure side, while the other tap is on the low pressure side. The
difference between these two pressures is called the differential pressure and is a function of the amount of
air mass (air density) flowing through the orifice. Usually, we don’t worry about air density for typical ambient
temperatures and pressures encountered in duct leakage measurements. The error in measurement is very
small for temperatures from 50 to 120 degrees F, and elevations up to 1200 feet.
If you are leak testing a system in high elevations such as Denver, or performing a leak test with unusually
high air temperatures, a density correction must be made. ORIFLOW can supply data for your ORIFLOW
orifice or orifice tube so that it is adjusted or corrected for your particular environment. If you have purchased
one of our testers, we supply free of charge an Adobe PDF form that will automatically make those corrections
for you as well as calculate duct surface area and other parameters.